I have just purchased a 7KVA generator set to replace my old one on my marine electrical system. The unit is supplied connected M.E.N. internally with output supply connected to a bipole circuit breaker.
As the connections between earth and neutral is before the the breakers, there is no allowance for the earth wire from the appliance side to connect to on the genset. Should I wire this appliance earth onto the frame of the genset or leave it ‘floating’?
The green, earth wire from your AC system needs to be connected to the chassis of the new generator. It should not be floating. With AC systems, the neutral and ground are connected at the source of power (the generator). The neutral and ground remain separate on the rest of the boat. The neutral is connected through the breaker and the ground directly.
The reality is, once the generator battery ground is connected to the rest of the battery negatives on the boat, the green, earth wire path is complete. Your AC system green earth wire is already connected to the boat’s DC negative system. The negative generator cable is connected to the generator ground. The generator ground is connected to the generator’s earth ground.
Hope this helps,